StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-508; IEC 60811-509
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
Connection to electricity meters, aerial connection to electricity meters and electricity outlets to switches, in order to prevent energy theft.
1. Conductor: Soft copper, class 1 (wire) or class 2 (cable).
2. Insulation: Compound polyvinyl chloride PVC.
3. Inner sheath: Compound polyvinyl chloride PVC (for cables with more than two central cores).
4. Concentric conductor: Copper wires helically applied.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good dielectric strength, moisture and weather resistant, adequate resistance to grease and heat. Flame retardant. Resistance to sunlight.
From 2,5 mm2 up to 16 mm2.
INDECO S.A. SET 0,6/1 kV - (Nb. conductors + 01 Concentric cond.) x Section - Year - Sequential length.
Non returnable wooden reels.
For two-core cables: Natural.
For three-core cables: Natural and black.
For four-core cables: Natural, black and red.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3:FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods -Ageing in an air oven.
IEC 60811-402: Various tests. Water absorption test.
IEC 60811-501: Test for determining the mechanical properties of insulating and sheating.
IEC 60811-504: Bending test at low temperature for insulation and covers.
IEC 60811-505: Low temperature elongation test for insulations and covers.
IEC 60811-506: Impact test at low temperature for insulations and covers.
IEC 60811-508: High temperature pressure tests for insulations and covers.
IEC 60811-509: Mechanical tests. Tests of resistance to cracking of the insulations and covers.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
UL 2556:Wire and Cable Test Methods. Section 220.127.116.11:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Concentric conductor||Copper wires helically applied|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|