StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
General use as power cable. In low voltage distribution networks, industrial installations, buildings and operating centers. For fixed installations, in indoor areas (trays, ducts), in underground ducts or buried direct in ground, in dry or wet locations.
1. Conductor: Aluminium 1350, class 2.
2. Insulation: Compound polyvinyl chloride PVC.
3. Outer sheath: Compound polyvinyl chloride PVC.
4. Tape: Polyester tape.
Good electrical and mechanical properties. The PVC outer sheath provides an adequate resistance to grease, oils and abrasion. Cables with better dissipation of heat allowing a higher current capacity. Sunlight resistance. Flame retardant.
From 16 mm2 up to 150 mm2.
INDECO S.A. NAYY(80º)0,6/1 kV - 3-1x Section - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black, red and white.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3:FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods -Ageing in an air oven.
IEC 60811-402: Water absorption test.
IEC 60811-501: Test for determining the mechanical properties of insulating and sheating.
IEC 60811-504: Bending test at low temperature for insulation and covers.
IEC 60811-505: Low temperature elongation test for insulations and covers.
IEC 60811-506: Impact test at low temperature for insulations and covers.
IEC 60811-508: High temperature pressure tests for insulations and covers.
IEC 60811-509: Tests of resistance to cracking of the insulations and covers (thermal shock).
UL 2556:Wire and Cable Test Methods. Section 126.96.36.199:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Sheath colour||Individual sheath White-Black-Red|
|Time of application Dielectric strength core to screen DC||5min.|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Flame retardant||IEC 60332-1-2; FT1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|