StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034; IEC 61034-2
National : ABNT NBR 6251 ; ABNT NBR 7286 ; NTP-IEC 60228; UL 2556
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded aluminium 1350, class 2 (longitudinally watertight between and over conductor).
2. Inner semi-conductor: Extruded.
3. Insulation: High Density Ethylene-Propylene Rubber HEPR.
4. External semi-conductor: Extruded strippable.
5. Screen: Copper wires.
6. Tape: Polyester tape.
7. Outer sheath: Linear Low Density Polyethylene LLDPE Resist.UV
Resistance to abrasion, moisture and sunlight. Longitudinally watertight between and over conductor. Adequate resistance to greases and oils. The outer sheath has the following characteristics: low emission dense smoke and halogen free.
From 95 mm2 up to 630 mm2
INDECO S.A. NAGS2Y(OL) 20/35 kV - Section - PH(Section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
ABNT NBR 6251: Insulated power cables, for rated voltages 1 kV up to 35 kV - Constructive requirements.
ABNT NBR 7286: Power cables with extruded ethylene rubber insulation (EPR) for rated voltages from 1 kV up to 35 kV - Perfomance requirements.
IEC 60228: Conductors of insulated cables.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754: Test on gases evolved during combustion of materials from cables.
Part 1: Determination of the halogen acid gas content.
Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 188.8.131.52: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Halogen free||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Longitudinal water tightness||Yes|
|Maximum operating temperature||105°C|
|Overload maximum core temperature||140°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|