TECK 90 600 V Multi core with insulated ground conductor
General application as power cable in low voltage.
StandardsNational : CSA C22.2 N° 03-01; CSA C22.2 N° 131; CSA C22.2 N° 2556; CSA C22.2 N° 38; UL 2556
General application in low voltage distribution networks in operating stations where high mechanical strength is required. The interlocked aluminum armour gives greater flexibility compared to the traditional steel armour and the type of conformation of the same make has a high resistance to loads that could be placed on it.Class I, Div.2 and Class II, Div.2 hazardous locations per NEC.
1. Conductor: Soft copper, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. Insulated grounding conductor: Soft copper, class B - Insulated with XLPE
4. Inner covering: Anti-flame compound polyvinyl chloride PVC.
5. Armour: Interlocked aluminum tape.
6. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Resistance to abrasion and oils. Resistance to weather and sunlight. Its armour provides additional mechanical protection and provides greater flexibility compared with other types of armour. Does not propagate the FT-1 flame. Fire retardant according to C22.2 No 0.3-01/FT-4. Resistance to attack by rodents.
From 14 AWG up to 500 kcmil.
For gauges equal to or smaller than 8 AWG: INDECO S.A. TECK 90(XLPE) (Nb. cores x Gauge phase cond. + Gauge ground. cond.) 0,6 kV -25C FT1 FT4 SR CSA 255079 - Year - Sequential length.
For gauges higher than 8 AWG: INDECO S.A. TECK 90(XLPE) (Nb. cores x Gauge phase cond. + Gauge ground. cond.) 0,6 kV -40C FT1 FT4 SR CSA 255079 - year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
CSA C22.2 Nº 131-14: Type TECK 90 cable.
CSA C22.2 Nº 38-14: Thermoset-insulated wires and cables.
CSA C22.2 Nº 03-01: Test methods for electrical wires and cables.
CSA C22.2 Nº 2556-15: Wire and cable test methods.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Insulating material||Flame retardant XLPE|
|Inner sheath||Flame retardant PVC|
|Armour type||Interlocked aluminum tape|
|Outer sheath||Flame retardant PVC|
|Mechanical resistance to impacts||Excellent|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||FT4 (C22.2 No. 0.3-01/4.11.4)|
|Bending factor when installed||7(xD)|
|Rodent protection||Corrugated aluminium tape|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Number of cores
White + black or black with white numbers for control cable + (yellow or green)
(White or blue) + black + red or black with white numbers for control cable + (yellow or green)
White + black + red + blue or black with white numbers for control cable + (yellow or green)
Black with white numbers for control cable + (yellow or green)