FREETOX N2XOH-C 0.6/1 kV CAT. A
Special application in places with poor ventilation and places public attendance high.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60332-3 Cat.A; IEC 60502-1; IEC 60684-2; IEC 60754-2; IEC 60811-1-1; IEC 60811-1-2; IEC 60811-1-3; IEC 60811-1-4; IEC 60811-2-1; IEC 60811-3-1; IEC 61034
National : NTP-IEC 60228; NTP-IEC 60502-1
In industrial plants, for systems of motor control, lighting, signaling and overal equipment interconnection, control circuits of automatic machines. Direct application in places with public attendance high. Not recommended for outdoor installations
1. Conductor: Copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Filler: HFFR Halogen free thermoplastic compound.
4. Outer sheath: HFFR Halogen free thermoplastic compound.
Conductor temperature of 250°C for short circuit conditions. Lower dielectric losses, high insulation resistance. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Resistance to sunlight.
INDECO S.A FREETOX N2XOH-C 0.6/1 kV N° Conductors x Section.
Non returnable wooden reels.
Insulation: Black with white numbers.
Outer sheath: Black-UV.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-1-2: Tests on electrical and optical fibre cables under fire conditions - Part 1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
IEC 60332-3-22: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category A.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60684-2: Flexible insulating sleeving - Methods of test.
IEC 60754-2: Determination of degree of acidity of gases evolved during the combustion of materials taken from electric cables by measuring pH and conductivity.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-1-2: Thermal ageing methods.
IEC 60811-1-3: Water absorption tests - Shrinkage test.
IEC 60811-1-4: Tests at low temperature.
IEC 60811-2-1: Ozone resistance, hot set and mineral oil immersion tests.
IEC 60811-3-1: Pressure test at high temperature - Tests for resistance to cracking.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
|Core identification||Black cores with white numbers|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-2|
|Minimum insulation thickness||0.7mm|
|Minimum outer sheath thickness||1.2mm|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Smoke density||IEC 61034|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.A|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|