N2XY 0,6/1 kV Single core; IEC 60332-3-24 Cat. C
General use as power cable, for fixed installations.
StandardsInternational : FT4 IEEE1202 ; IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60754-1; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-1; SAE J-1127; UL 2556; UL 44
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Compact soft copper, class 2.
2. Insulation: Anti-flame cross linked polyethylene XLPE.
3. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dielectric losses, high insulation resistance. The PVC outer sheath allows an adequate resistance to abrasion, moisture and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Fire retardant according to IEC 60332-3-24 Cat. C.
From 16 mm2 up to 400 mm2.
INDECO S.A. N2XY 0,6/1 kV - Section - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
FT4/IEEE 1202: Vertical Tray Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UL 2556:Wire and Cable Test Methods. Section 126.96.36.199:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Insulating material||Flame retardant XLPE|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||UIC 895 OR|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|