StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
Connection to electricity meters, aerial connection to electricity meters and electricity outlets to switches, in order to prevent energy theft.
1. Conductor: Soft copper, class 1.
2. Insulation: Compound polyvinyl chloride PVC.
3. Inner sheath: Compound polyvinyl chloride PVC (for three-core cables only).
4. Concentric conductor: Copper wires helically applied.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good dielectric strength, moisture and weather resistant, adequate resistance to grease and heat. Flame retardant.
From 4 mm2 up to 10 mm2.
INDECO S.A. SET 0,6/1 kV - (Nb. central conductors + 01 concentric cond.) x Section - Year - Sequential length.
Non returnable wooden reels.
For two-core cables: Natural.
For three-core cables: Natural and black.
Outer sheath: Black.
DNC-ET-010a: Standard specification - Copper concentric cables with insulation and sheaths of PVC.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-504: Tests at low temperature.
IEC 60811-505: Tests at low temperature.
IEC 60811-506: Tests at low temperature.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
UL 2556:Wire and Cable Test Methods. Section 188.8.131.52:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Concentric conductor||Copper wires helically applied|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|