StandardsInternational : IEC 60228; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-502; IEC 60811-503; IEC 60811-507; IEC 60811-605
National : NTP-IEC 60228; NTP-IEC 60502-1
Connection to electricity meters, aerial connection to electricity meters and electricity outlets to switches, in order to prevent energy theft.
1. Conductor: Soft copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Concentric conductor: Copper wires helically applied.
4. Tape: Polyester.
5. Outer sheath: Cross linked polyethylene XLPE.
Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dielectric losses, high insulation resistance. Resistance to abrasion, weather and sunlight.
From 6 mm2 up to 16 mm2.
INDECO S.A. N2XC2X 0,6/1 kV - ( Nb. conductors x section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
NTCRE 010/11: XLPE insulated copper concentric cable 1F.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-503: Shrinkage test for sheaths.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-605: Measurement of carbon black and / or mineral filler in polyethylene compounds.
|Conductor material||Soft copper|
|Concentric conductor||Copper wires helically applied|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|