NA2XY 0,6/1 kV; Double or Triple; DNC-ET-094a
General use as power cable, for fixed installations.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-409; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
General use as power cable. In low voltage distribution networks, industrial installations, buildings and operating centers. For fixed installations, in indoor areas (trays, ducts), in underground ducts or buried direct in ground, in dry or wet locations.
1. Conductor: Compact aluminium 1350, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Outer sheath: Compound polyvinyl chloride PVC.
4. Tape: Polyester tape.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dielectric losses, high insulation resistance. The PVC outer sheath allows an adequate resistance to greases, oils, abrasion and sunlight. Flame retardant.
From 10 mm2 up to 500 mm2.
INDECO S.A. NA2XY 0,6/1 kV - (2 or 3) - 1 x Section - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: White and black or white, black and red.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
DNC-ET-094a: Luz del Sur Standard - Cable with XLPE insulated NA2XY Underground network L.V. 220 V.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods-Ageing in an air oven.
IEC 60811-402: Water absorption test.
IEC 60811-409: Loss of mass test for thermoplastic insulations and sheaths.
IEC 60811-501: Test for determining the mechanical properties of insulating and sheathing.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-504: Bending test at low temperature for insulation and covers.
IEC 60811-505: Low temperature elongation test for insulations and covers.
IEC 60811-506: Impact test at low temperature for insulations and covers.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-508: High temperature pressure tests for insulations and covers.
IEC 60811-509: Tests of resistance to cracking of the insulations and covers (thermal shock).
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 18.104.22.168: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|