NYCY(80°) 0.6/1 kV
In factories, substations or power plants. Application as power and control cable in VFD.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60502-1; IEC 60811-1-1; IEC 60811-1-2; IEC 60811-1-3; IEC 60811-1-4; IEC 60811-3-1; IEC 60811-3-2
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 1581
In factories, substations or power plants where there is a lot of electrical noise or transiet, for control. measuring or signaling systems, for connection between the variable frequency drive (VFD) and the motor; reduce to electromagnetic interferences.
1. Conductor: Copper, class 2.
2. Insulation: Compound polyvinyl chloride PVC.
3. Inner covering: Compound polyvinyl chloride PVC.
4. Screen: Copper wires + copper tape.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Resistance to moisture, abrasion and sunlight. Adequate resistance to grease and oil. Good transient shield. Flame retardant.
From 95 mm2 up to 240 mm2.
INDECO S.A. NYCY(80°) 0.6/1 kV - (Nbcores x section) + conc. cond. section - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black, red and white.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-1-2: Thermal ageing methods.
IEC 60811-1-3: Water absorption tests - Shrinkage test.
IEC 60811-1-4: Tests at low temperature.
IEC 60811-3-1: Pressure test at high temperature - Tests for resistance to cracking.
IEC 60811-3-2: Loss of mass test - Thermal stability test.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Core identification||Black, red, white|
|Concentric conductor||Copper wires helically applied|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Flame retardant||IEC 60332-1|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Electro magnetic interference resistance||Yes|
|Max. conductor temperature in service||80°C|
|See all products|