N2XSY-C 0,6/1 kV; Screen electr. resist. PH: 2,0 Ohm/km
In factories, for control systems.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-409; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In factories, for systems of motor control, lighting, signaling and overal equipment interconnection, control circuits of automatic machines.
1. Conductor: Soft compressed copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Inner covering: Compound polyvinyl chloride PVC.
4. Screen: Copper wires.
5. Tape: Polyester.
6. Outer sheath: Compound polyvinyl chloride PVC.
The cross-linked polyethylene insulation allows greater current capacity in any operating condition, minimum dielectric losses, high insulation resistance. The outer PVC cover gives it an adequate resistance to fats, oils, moisture and abrasion. Resistance to sunligth. Flame retardant.
2.5 mm2 and 4 mm2.
INDECO S.A. N2XSY-C 0.6/1 kV - Nb. Conductors x Section - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black with white numbers.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-409: Loss of mass test for thermoplastic insulations and sheaths.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-504: Tests at low temperature.
IEC 60811-505: Tests at low temperature.
IEC 60811-506: Tests at low temperature.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
UL 2556: Wire and Cable Test Methods. Section 220.127.116.11: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Core identification||Black cores with white numbers|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Resistance of the screen||2.0Ohm/km|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|