StandardsInternational : IEC 60332-1-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-70-547; NTP 370.258; UL 2556
Primary and secundary distribution networks, Outdoors installations in industrial plants, mines, etc. This is not an insulated cable, it is a protected cable.
1. Conductor: All Alloy Aluminium 6201, class 2.
2. Sheath: Low linear density polyethylene LLDPE-UV.
Excellent properties to withstand outdoor conditions such as moisture, ozone, sunlight and heat. Resistance to fatigue, fungus and abrasion. low emission dense smoke and halogen free. Adequate resistance to greases and oils. Flame retardant. Protection should not be considered as insulation.
From 25 mm2 up to 120 mm2.
Non returnable wooden reels.
NTP 370.258: Conductors with aluminum round wires stranded concentrically for overhead networks.
IPCEA S-70-547: Specifications for weather-resistant polyolefin-covered wire and cable.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754: Test on gases evolved during combustion of materials from cables.
Part 1: Determination of the halogen acid gas content.
Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum alloy|
|Halogen free||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Bending factor when installed||4(xD)|
|Maximum operating temperature||75°C|
|Overload maximum core temperature||90°C|
|Short-circuit max. conductor temperature||130°C|
|See all products|