CAAI 600 V Covered Neutral without Public Lighting; CGE
For overhead secundary distribution networks.
StandardsInternational : IEC 60228; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-502; IEC 60811-507; IEC 60811-605
National : NTP-IEC 60228
For urban and rural overhead secundary distribution networks, with voltages up to 600 V.
1. Conductor: Compact aluminium 1350, class 2.
2. Insulated neutral messenger: AAAC - All Alloy Aluminium insulated with cross-linked polyethylene XLPE.
3. Insulation: Cross linked polyethylene XLPE.
Decreases energy theft, cross-linked polyethylene allows more current capacity and high insulation resistance, lower inductive reactance than with bare conductors, used in overhead distribution lines. Increased safety due to its mechanical strength and toughness of the insulation. Insulators are not necessary for installation. Resistance to abrasion, weather and sunlight.
From 16 mm2 up to 120 mm2.
INDECO S.A CAAI 600 V - (Nb. Cores x Section) + NA(Neutral messenger section) - Year - Sequential length.
Non returnable wooden reels.
Black, see core identification.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-605: Measurement of carbon black and/or mineral filler in polyethylene compounds.
|Phase Conductor Type||Aluminium 1350|
|Core identification||Rib markings|
|Neutral messenger||Alloy Aluminium|
|Dielectric strength core to screen DC, min.||4.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Bending factor when installed||4(xD)|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|