MULTIPLEX-ACSR 600 V, Bare Neutral; Insulation: LLDPE
For overhead secundary distribution networks.
StandardsInternational : IEC 60332-1-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ASTM B 231; ASTM B 232; ICEA S-76-474; ICEA S-93-639; UL 2556
For urban and rural overhead secundary distribution networks, with voltages up to 600 V.
1. Conductor: Compact aluminium 1350, class B.
2. Bare neutral messenger ACSR: Aluminium 1350 - Core: galvanized stranded steel wire.
3. Insulation: LLDPE-UV Low Linear Dendsity Polyethylene
Decreases energy theft, Polyethylene is a very good insulation as it offer a very high insulation resistance, used in overhead distribution lines. Insulators are not necessary for installation. Resistance to impact, weather and sunlight.
From 6 AWG up to 3/0 AWG.
INDECO S.A. - "Code name" - 600 V - (Nb. cores x gauge) + ND (Neutral gauge ACSR) - Year - Sequential length.
Non returnable wooden reels.
Black, see core identification.
ASTM B231: Concentric-Lay-Stranded Aluminum 1350 Conductors.
ASTM B232: Concentric-Lay-Stranded Aluminum Conductors, Coated-Steel Reinforced (ACSR).
ICEA S-76-474: Standard for neutral-supported power cable assemblies with weather-resistant extruded insulation rated 600 V.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables. Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables. Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 220.127.116.11: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Phase Conductor Type||AAC - All Aluminium Conductor|
|Core identification||Rib markings|
|Neutral messenger||ACSR - Aluminum Conductor Coated Steel Reinforced|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||1min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Bending factor when installed||4(xD)|
|Maximum operating temperature||75°C|
|See all products|