FREETOX N2XOH-C 0,6/1 kV FB; AWG
Special application in places with poor ventilation and places public attendance high.
StandardsInternational : IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-95-658; NTP 370.250; NTP-IEC 60502-1
In industrial plants, for systems of motor control, lighting, signaling and overal equipment interconnection, control circuits of automatic machines. Direct application in places with public attendance high.Not recommended for outdoor installations
1. Conductor: Flexible soft copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. Filler: HFFR halogen free thermoplastic compound.
4. Outer sheath: HFFR halogen free thermoplastic compound.
Lower dielectric losses, high insulation resistance. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils.
INDECO S.A FREETOX N2XOH-C 0,6/1 kV - Nb. conductors x gauge - FB - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black with white numbers.
Outer sheath: Black.
NTP 370.250: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables. Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables. Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil: Oil Immersion Test.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Core identification||Black cores with white numbers|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||5min.|
|Oil resistance||ICEA S-95-658|
|Gases corrosivity||IEC 60754-2|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|