StandardsInternational : IEC 60228; IEC 60332-1; IEC 60502-1; IEC 60811-1-1; IEC 60811-1-2; IEC 60811-1-3; IEC 60811-1-4; IEC 60811-2-1; IEC 60811-3-1; IEC 60811-3-2
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 1581
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operating stations, indoor and outdoor areas. It can be installed in ducts, in dry or wet locations, where mechanical strength is requiered.
1. Conductor: Soft copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Inner covering: Compound polyvinyl chloride PVC.
4. Armour: Galvanized steel tapes.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dielectric losses, high insulation resistance. Its armour provides additional mechanical protection. The PVC outer sheath allows an adequate resistance to greases, oils, abrasion and sunlight. Flame retardant.
From 6 mm2 up to 50 mm2.
INDECO S.A. N2XBY 0,6/1 kV - Nb. Cores x section - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables
NPT-IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3kV.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3 kV.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-1-2: Thermal ageing methods.
IEC 60811-1-3: Water absorption tests - Shrinkage test.
IEC 60811-1-4: Tests at low temperature.
IEC 60811-2-1: Ozone resistance, hot set and mineral oil inmersion tests.
IEC 60811-3-1: Pressure test at high temperature - Tests for resistance to cracking.
IEC 60811-3-2: Loss of mass test - Thermal stability test.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Armour type||Steel tapes|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Flame retardant||IEC 60332-1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Core Identification L.V
Number of cores
White + black, black + blue, blue + brown or black + red
White + black + red, brown + black + grey, blue + brown + black or black + red + blue
White + black + red + blue or blue + brown + black + grey
White + black + red + blue + brown