NGY 0,6/1 kV Single-core; AWG/kcmil
General use as power cable in low voltage, for fixed installations.
StandardsInternational : IEC 60332-1-2; IEC 60502-1; IEC 60754-1; IEC 60811-401; IEC 60811-402; IEC 60811-403; IEC 60811-409; IEC 60811-501; IEC 60811-503; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : ASTM B 8; NTP-IEC 60228; NTP-IEC 60502-1; UL 1685; UL 2556
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Compact soft copper, class B.
3. Insulation: High Ethylene Polyethylene Rubber HEPR.
3. Outer sheath: Low Smoke, low halogen, flame retardant PVC compound.
HEPR increased safety due to its mechanical strength and toughness of the insulation. Adequate resistance to greases, oils and abrasion. Resistance to sunlight. The outer sheath has the following characteristics: Flame retardant, low emission dense smoke and low halogen content.
From 4 AWG up to 750 kcmil.
INDECO S.A. NGY 0,6/1 kV - Gauge - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black-UV.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3:FT1 (Vertical-Specimen) Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60811-401: Thermal ageing methods -Ageing in an air oven.
IEC 60811-402: Water absorption test.
IEC 60811-403: Test of ozone resistance on cross-linked components.
IEC 60811-409: Mass loss test for thermoplastic insulations and covers.
IEC 60811-501: Test for determining the mechanical properties of insulating and sheating.
IEC 60811-504: Bending test at low temperature for insulation and covers.
IEC 60811-505: Low temperature elongation test for insulations and covers.
IEC 60811-506: Impact test at low temperature for insulations and covers.
IEC 60811-507: Hot elongation test for crosslinked materials.
IEC 60811-508: High temperature pressure tests for insulations and covers.
IEC 60811-509: Tests of resistance to cracking of the insulations and covers (thermal shock).
UL 1685: Standard for Vertical-Tray Fire-Propagation and Smoke-Release Test for Electrical and Optical-Fiber Cables.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||105°C|
|Overload maximum core temperature||140°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|