NYY(80º) 0,6/1 kV FB Multicore with grounding conductor
General use as power cable, for fixed installations.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-501; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
General use as power cable. In low voltage distribution networks, industrial installations, buildings and operating centers. For fixed installations, in indoor areas (trays, gutters, staples), outdoors, in underground ducts or buried direct in ground. It can also be installed in dry or wet locations.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: Compound polyvinyl chloride PVC.
3. Insulated grounding conductor: Copper - PVC.
4. Filler: Compound polyvinyl chloride PVC.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. The PVC outer sheath provides an adequate resistance to grease, oils and abrasion. Resistance to sunlight. Flame retardant.
From 4 mm2 up to 35 mm2.
INDECO S.A. NYY(80º) 0,6/1 kV - (N° cores x section) + ground section - FB - Year.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-504: Bending test at low temperature for insulation and sheaths.
IEC 60811-505: Elongation at low temperature for insulations and sheaths.
IEC 60811-506: Impact test at low temperature for insulations and sheaths.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|
Products and services
Docs and info
Core Identification NYY(80°) 0,6/1 kV with earth cond.
Number of cores
White + black + (yellow or green or yellow/green or green/yellow)
White + black + red + (yellow or green or yellow/green or green/yellow)
White + black + red + blue + (yellow or green or yellow/green or green/yellow)