StandardsInternational : IEC 60228; IEC 60332-1; IEC 60502-1; IEC 60811-1-1; IEC 60811-1-2; IEC 60811-1-3; IEC 60811-1-4; IEC 60811-2-1; IEC 60811-3-1; IEC 60811-3-2
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 1581
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operating stations, indoor and outdoor areas. It can be installed in ducts, in dry or wet locations where mechanical strength is requiered.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. Inner covering: Compound polyvinyl chloride PVC.
4. Armour: Galvanized steel wires.
5. Tape: Polyester.
6. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operation condition, minimum dilectric losses, high insulation resistance. Its armour provides additional mechanical protection. The PVC outer sheath allows an adequate resistance to greases, oils and abrasion. Resistance to sunlight. Flame retardant.
From 4 mm2 up to 95 mm2.
INDECO S.A. N2XRY 0,6/1 kV - Nb. Cores x cross section - Year - Sequential Length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables
NPT-IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-409: Loss of mass test for thermoplastic insulations and sheaths.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-504: Bending test at low temperature for insulation and sheaths.
IEC 60811-505: Elongation at low temperature for insulations and sheaths.
IEC 60811-506: Impact test at low temperature for insulations and sheaths.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Armour type||Galvanized steel wires|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Core Identification L.V
Number of cores
White + black, black + blue, blue + brown or black + red
White + black + red, brown + black + grey, blue + brown + black or black + red + blue
White + black + red + blue or blue + brown + black + grey
White + black + red + blue + brown