NGY 600 V Multicore with insulated grounding cond.; Outer sheath PVC antiflame
General use as power cable in low voltage, for fixed installations.
StandardsInternational : IEC 60332-1-2; IEC 60754-1; UIC 895
National : ASTM B 8; ICEA S-95-658; SAE J-1127; UL 2556; UL 44
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Soft copper, class B.
2. Insulation: High Ethylene Polyethylene Rubber HEPR.
3. Insulated grounding conductor: Soft copper, class B - HEPR.
4. Filler: PVC compound(as applicable).
5. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Resistance to abrasion, moisture and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Flame retardant.
From 12 AWG up to 250 kcmil.
INDECO S.A. NGY 0,6 kV - (Nb. Cores x gauge) + gauge ground. cond. - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 22.214.171.124:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Outer sheath||Flame retardant PVC|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||UIC 895 OR|
|See all products|
Products and services
Docs and info
Core Identification L.V with ground cond.
Number of cores
Black + (yellow or green or yellow/green or green/yellow)
White + black, white + red, white + blue, blue + brown, blue + black or black + red + (yellow or green or yellow/green or green/yellow)
White + black + red, black + red + blue, brown + black + grey or blue + brown + black + (yellow or green or yellow/green or green/yellow)
White + black + red + blue, blue + brown + black + grey + (yellow or green or yellow/green or green/yellow)