N2XY 600 V Multicore with Insulated Ground cond; FT4/IEEE 1202
General use as power cable, for fixed installations.
StandardsInternational : FT4 IEEE1202 ; IEC 60332-1-2; IEC 60754-1; UIC 895
National : ASTM B 8; ICEA S-95-658; SAE J-1127; UL 2556; UL 44
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Soft copper, class B.
2. Insulation: Anti-flame cross linked polyethylene XLPE.
3. Insulated grounding conductor: Soft copper, class B - Anti-flame XLPE.
4. Tape: Polyester.
5. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operating condition. Resistance to abrasion, moisture and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Fire retardant according to IEEE 1202/FT-4.
From 12 AWG AWG up to 1 AWG.
INDECO S.A. N2XY 0.6 kV - Nb. Cores x Gauge + Ground Cond. Gauge - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
FT4/IEEE 1202: Vertical Tray Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 184.108.40.206:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Insulating material||Flame retardant XLPE|
|Outer sheath||Flame retardant PVC|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||FT4/IEEE 1202|
|Oil resistance||UIC 895 OR|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Core Identification L.V with ground cond.
Number of cores
Black + (yellow or green or yellow/green or green/yellow)
White + black, white + red, white + blue, blue + brown, blue + black or black + red + (yellow or green or yellow/green or green/yellow)
White + black + red, black + red + blue, brown + black + grey or blue + brown + black + (yellow or green or yellow/green or green/yellow)
White + black + red + blue, blue + brown + black + grey + (yellow or green or yellow/green or green/yellow)