NA2XSY(2OL) 18/30 kV PH+PC; UTE NO-DIS-MA-1502
Cable for underground power distribution and subtransmission.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-2; IEC 60811-401; IEC 60811-402; IEC 60811-409; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : ICEA S-93-639; ICEA T-34-664; NTP-IEC 60228; NTP-IEC 60502-2; UL 2556
Underground power distribution and subtransmission. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact round aluminium 1350, class 2 (Longitudinally watertight between and over conductor).
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper wires + copper tape in open spiral (longitudinally watertight under and over screen).
6. Outer sheath: Compound polyvinyl chloride PVC.
Excellent properties against heat aging. Resistance to abrasion and moisture. Longitudinally watertight between and over conductor, and under and over screen. Adequate resistance to greases and oils. Flame retardant.
240 mm2 and 500 mm2.
INDECO S.A. NA2XSY(2OL) 18/30 kV - Section - PH(Section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Red.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60228: Conductors of insulated cables.
NO-DIS-MA-1502: Unipolar underground cables with dry insulation. High voltage networks up to 36 kV.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-409: Loss of mass test for thermoplastic insulations and sheaths.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-504: Bending test at low temperature for insulation and sheaths.
IEC 60811-505: Elongation at low temperature for insulations and sheaths.
IEC 60811-506: Impact test at low temperature for insulations and sheaths.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
UL 2556: Wire and Cable Test Methods. Section 188.8.131.52: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
ICEA T-34-664: Test Method for Conducting Longitudinal Water Penetration Resistance Tests on Longitudinal Water Blocked Cables.
|Conductor material||Aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper wire + copper tape|
|Rated Voltage Uo/U (Um)||18/30 kV|
|Dielectric strength core to screen DC, min.||63.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||31.1kV|
|Maximal partial discharge test||10pC|
|Cable flexibility||Class 2 IEC 60228|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-93-639|
|Longitudinal water tightness||Conductor and screen ICEA T-34-664|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|