N2XSY 0,6/1 kV FB Single-core; AWG
General use as power cable in low voltage, for fixed installations.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-409; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. Inner covering: Compound polyvinyl chloride PVC.
4. Screen: Copper tapes.
5. Outer sheath: Compound polyvinyl chloride PVC.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dielectric losses, high insulation resistance. The PVC outer sheath allows an adequate resistance to greases, oils and abrasion. Sunlight resistance. Flame retardant.
From 2 AWG up to 3/0 AWG.
INDECO S.A. N2XSY 0,6/1 kV - Gauge - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-409: Loss of mass test for thermoplastic insulations and sheaths.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-504: Bending test at low temperature for insulation and sheaths.
IEC 60811-505: Elongation at low temperature for insulations and sheaths.
IEC 60811-506: Impact test at low temperature for insulations and sheaths.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Conductor flexibility||Flexible class 5|
|Screen||Copper tape, helically|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|