N2XSY 0,6/1 kV FB; 3F + 3T
Power or control cable, for use with variable frequency drives (VFD).
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-409; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In factories, substations or power plants where there is a lot of electrical noise or transiet, for control, measuring or signaling systems, for connection between the variable frequency drive (VFD) and the motor; reduce to electromagnetic interferences.
1. Conductor: Flexible soft copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. 03 Bare grounding conductors: Soft copper, class 5.
4. Inner covering: Compound polyvinyl chloride PVC.
5. Screen: Copper tape(30mm x 0,127mm) 50% overlapped.
6. Outer sheath: Compound polyvinyl chloride PVC.
Excellent properties against heat aging. Excellent transient shield. The PVC outer sheath allows an adequate resistance to greases, oils and abrasion. Resistance to sunlight. Flame retardant.
From 2,5 mm2 up to 120 mm2.
INDECO S.A N2XSY 0,6/1 kV - Nb. Cores x Section + 03 x Ground section Cond. - FB - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black, white and red.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-409: Loss of mass test for thermoplastic insulations and sheaths.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-504: Bending test at low temperature for insulation and sheaths.
IEC 60811-505: Elongation at low temperature for insulations and sheaths.
IEC 60811-506: Impact test at low temperature for insulations and sheaths.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Copper class 5|
|Conductor flexibility||Flexible class 5|
|Electrostatic shielding||Copper tapes helically applied|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Electro magnetic interference resistance||Yes|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|