N2XSY 0,6/1 kV FB; 3F + 3T
Power or control cable, for use with variable frequency drives (VFD).
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; IEC 60811-401; IEC 60811-402; IEC 60811-409; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In factories, substations or power plants where there is a lot of electrical noise or transiet, for control, measuring or signaling systems, for connection between the variable frequency drive (VFD) and the motor; reduce to electromagnetic interferences. Maximum operating temperature 90°C, in dry or wet locations.
1. Conductor: Soft copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. 03 Bare grounding conductors: Soft copper, class 5.
4. Inner covering: Compound polyvinyl chloride PVC.
5. Screen: Copper tape(30mm x 0,127mm) 50% overlapped.
6. Outer sheath: Compound polyvinyl chloride PVC.
Excellent transient shield. Resistance to moisture, abrasion, oil and sunlight. Flame retardant.
From 2.5 mm2 up to 120 mm2.
INDECO S.A N2XSY 0,6/1 kV - (Nb. cores x section) + (03 x Ground section cond.) - FB - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black, white and red.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-409: Loss of mass test for thermoplastic insulations and sheaths.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-504: Bending test at low temperature for insulation and sheaths.
IEC 60811-505: Elongation at low temperature for insulations and sheaths.
IEC 60811-506: Impact test at low temperature for insulations and sheaths.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
UL 2556: Wire and Cable Test Methods. Section 220.127.116.11: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Copper class 5|
|Electrostatic shielding||Copper tapes helically applied|
|Conductor flexibility||Flexible class 5|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Dielectric strength core to screen DC, min.||3.5kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Electro magnetic interference resistance||Yes|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|