StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60811-501; IEC 60811-502; IEC 60811-504; IEC 60811-505; IEC 60811-506; IEC 60811-507; IEC 60811-508; IEC 60811-509
National : ICEA S-93-639; ICEA T-31-610; IRAM 2178; IRAM 63004
Medium voltage aerial power distribution. Feeders in places where underground networks cannot be possible, mining installations, tree-lined urban zones or with little space.
1. Conductor: Compact stranded aluminum 1350, class 2 (With longitudinally watertight between and over the conductor).
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper wires + copper tape in open spiral.
6. Tape: Polyester.
7. Phase outer sheath: Compound polyvinyl chloride PVC.
8. Messenger: Galvanized stranded steel wire.
9. Messenger sheath: Compound polyvinyl chloride PVC.
Good resistance to traction. Resistance to abrasion and sunlight. Flame retardant.
From 50 mm2 up to 120 mm2.
INDECO S.A. NA2XSY(OL)-S 10,5/13,2 kV 3x1xSection - PH(Section) - Year - Sequential length.
Non returnable wooden reels.
Insulation: Natural (Core identification with binder tape).
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
IRAM 2178-2: Isolated Power Cables with Dielectric Solid Extruded for nominal voltages from 1,1 kV to 33 kV. Part 2: Power cables for nominal voltages from 3,3 kV (3,6 kV) to 33 kV (36 kV)
IRAM 63004: Preassembled cables for aerial distribution of electric power for nominal voltages from 13.2 kV to 33 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
IEC 60811-401: Thermal ageing methods. Ageing in an air oven.
IEC 60811-402: Water absorption tests.
IEC 60811-409: Loss of mass test for thermoplastic insulations and sheaths.
IEC 60811-501: Test for determining the mechanical properties.
IEC 60811-502: Shrinkage test for insulations.
IEC 60811-504: Bending test at low temperature for insulation and sheaths.
IEC 60811-505: Elongation at low temperature for insulations and sheaths.
IEC 60811-506: Impact test at low temperature for insulations and sheaths.
IEC 60811-507: Hot set test for cross-linked materials.
IEC 60811-508: Pressure test at high temperature for insulation and sheaths.
IEC 60811-509: Test for resistance of insulations and sheaths to cracking.
ICEA S-93-639: 5-46kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil inmersion test.
UL 2556: Wire and Cable Test Methods. Section 184.108.40.206: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
ICEA T-31-610: Test method for conducting longitudinal water penetration resistance tests on blocked conductors.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper wire + copper tape|
|Messenger||Galvanised stranded steel wire|
|Rated Voltage Uo/U (Um)||10.5/13.2 kV|
|Dielectric strength core to screen DC, min.||26.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||21.0kV|
|Maximal partial discharge test||5pC|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||ICEA S-93-639|
|Longitudinal water tightness||Conductor ICEA T-31-610|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|