FREETOX N2XSOHRAOH 8.7/15 kV FB; for instalation in vertical drilling mines
Cable for underground power distribution and subtransmission.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60332-3-24; IEC 60502-2; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034
National : ICEA S-93-639; NTP-IEC 60228; NTP-IEC 60502-2
Power distribution in medium voltage, direct application in places with public attendance high where high mechanical strength is required; for instalation in vertical drilling mines. Not recommended for outdoor installations.
1. Conductor: Soft copper, class 5.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
5. Screen: Copper tapes.
6. Separation sheath: HFFR thermoplastic compound.
7. 1st Layer armour: Aluminium 1350 wires.
8. 2nd Layer armour: Aluminium 1350 wires.
9. Tape: Polyester.
10. Outer sheath: HFFR thermoplastic compound.
Conductor temperature of 90ºC for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Its armour provides additional mechanical protection. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils.
INDECO S.A. FREETOX N2XSOHRAOH 8,7/15 kV - Section - FB - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Red.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
ICEA S-93-639 Section 9.4.2 (Oil Immersion Test): 5-46kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy - Oil Immersion Test.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 60811-3-1: Pressure test at high temperature - Tests for resistance to cracking.
IEC 60811-3-2: Loss of mass test - Thermal stability test.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
|Conductor material||Copper class 5|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper tape, helically|
|Armour type||Aluminium Wire|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Conductor flexibility||Flexible class 5|
|Rated Voltage Uo/U (Um)||8.7/15 kV|
|Mechanical resistance to impacts||Good|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Smoke density||IEC 61034-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.C|
|Oil resistance||ICEA S-93-639|
|Maximum operating temperature||90°C|
|See all products|
Products and services
Docs and info
Conditions for installation in vertical drilling mines M.V.