StandardsNational : ASTM B 231; UL 1072; UL 1581
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact round 1350 aluminium, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper tapes.
6. 03 Bare grounding conductors: Compact soft copper, class B.
7. Filler: Compound polyvinyl chloride PVC.
8. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Conductor temperature of 90ºC for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Excellent properties against heat aging. To 133% for insulation level. Resistance to abrasion; moisture and sunlight. Fire retardant.
From 4 AWG up to 4/0 AWG.
INDECO S.A. NA2XSEY 5 kV 133% I.L. - N° Conductors x Gauge - Year
Non returnable wooden reels.
Insulation: Natural (Cores are identified with binder tapes; color: red; white and black).
Outer sheath: Black.
ASTM B231: Standard Specification for Concentric-Lay-Stranded Aluminum 1350 Conductors.
FT4/IEEE 1202: Vertical Tray Flame Test.
UL 1072: Standard for Medium-Voltage Power Cables.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Outer sheath||Flame retardant PVC|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Fire retardant||FT4 (C22.2 No. 0.3-01/4.11.4)|
|Maximum operating temperature||90°C|
|See all products|