FREETOX N2XSOH-C 600 V AWG; UV Resist.
Special application in places with poor ventilation and places public attendance high.
StandardsInternational : IEC 60332-1; IEC 60332-3-24; IEC 60754-1; IEC 60754-2; IEC 61034
National : ASTM B 3; ASTM B 8; ICEA S-95-658; UL 1581
In industrial plants, for systems of motor control, lighting, signaling and overal equipment interconnection, control circuits of automatic machines. Direct application in places with public attendance high.
1. Conductor: Soft copper, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. Tape: Polyester tape.
4. Inner covering: HFFR thermoplastic compound.
5. Screen: Copper tapes.
6. Outer sheath: HFFR-UV thermoplastic compound.
The cable has excellent electric properties. The cross-linked polyethylene insulation allows a higher power capacity current under any operation conditions, lower dielectric losses, high insulation resistance. The filler and outer sheath have the following characteristics: Fire retardant, low emission dense smoke and halogen free. Resistance to sunlight. Adequate resistance to oil.
From 14 AWG up to 6 AWG.
INDECO S.A. N2XSOH-C 600 V - Nb. conductors x gauge - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black with white numbers.
Outer sheath: Black.
ASTM B3: Soft Annealed Copper Wire.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658 Section 6.4.2 (Oil Immersion Test): Power cables rated 2000 volts or less for the distribution of electrical energy - Oil Immersion Test.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60754-1: Determination of the amount of halogen acid gas evolved during the combustion of polymeric materials taken from cables.
IEC 60754-2: Determination of degree of acidity of gases evolved during the combustion of materials taken from electric cables by measuring pH and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Halogen free||IEC 60754-2|
|Inner sheath||Halogen free compound|
|Electrostatic shielding||Copper tapes helically applied|
|Outer sheath||Halogen free thermoplastic compound|
|Core identification||Black cores with white numbers|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Smoke density||IEC 61034-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.C|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|