N2XC2Y 0.6/1 kV FB; VFD
In factories, substations or power plants. Application as power and control cable in VFD.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60502-1; IEC 60811-1-2; IEC 60811-1-3; IEC 60811-2-1
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1
In factories, substations or power plants where there is a lot of electrical noise or transiet, for control. measuring or signaling systems, for connection between the variable frequency drive (VFD) and the motor; reduce to electromagnetic interferences.
1. Conductor: Flexible copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. Inner covering: LLDPE polyethylene.
4. Screen: Concentric conductor (copper wires) + Shield static (overlapped copper tape).
5. Outer sheath: LLDPE polyethylene.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dielectric losses, high insulation resistance. Excellent properties against heat aging. The LLDPE outer sheath allows an thermal and chemical good resistance. Resistance to abrasion, moisture and sunlight. Adequate resistance to abrasion and sunlight. Adequate resistance to greases and oils. Adequate transient shield. Flame retardant.
INDECO S.A N2XC2Y 0.6/1 kV - (Nbcores x section) + conc. cond. section - FB -Year - Sequential length.
Non returnable wooden reels.
Insulation: Red, white, black or White, black, blue or black with white numbers.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60811-1-2: Thermal ageing methods.
IEC 60811-1-3: Water absorption tests - Shrinkage test.
IEC 60811-2-1: Ozone resistance, hot set and mineral oil immersion tests.
ICEA S-95-658 Section 6.4.2 (Oil Immersion Test): Power cables rated 2000 volts or less for the distribution of electrical energy - Oil Immersion Test.
|Conductor flexibility||Flexible class 5|
|Screen||Copper wire + copper tape|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Electro magnetic interference resistance||Yes|
|Flame retardant||IEC 60332-1|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|