N2XSEYRAY 3,6/6 kV; IEC 60332-3-24 CAT.C; IEC 60502-2, UIC 895OR
Power distribution in medium voltage.
StandardsInternational : IEC 60332-1; IEC 60332-3 Cat.C; UIC 895
National : CSA C22.2 N° 131; NTP-IEC 60228; NTP-IEC 60502-2; UL 1581
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations; where mechanical strength is required.
1. Conductor: Compact stranded soft copper, class 2.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion.
5. Screen: Copper tapes.
6. Separation sheath: Anti-flame compound polyvinyl chloride PVC.
7. Armour: Aluminium 1350 wires.
8. Tape: Polyester tape.
9. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Conductor temperature of 90°C for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Excellent properties against heat aging. Its armour provides additional mechanical protection. Resistance to abrasion, moisture and sunlight. Resistance to oil according to UIC 895 OR. Low emission of acid gases, less than 14% by weight according to CSA C22.2 AG14. Fire retardant.
INDECO S.A. N2XSEYRAY 3,6/6 kV - Nb. cores x section - Year - Sequential length.
Non returnable wooden reels.
Insulation: Natural (Core identification with binder tapes: white, black, red).
Outer sheath: Red.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
CSA C22.2 AG14: Product rating for acid gas compliance.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-3-1: Pressure test at high temperature - Tests for resistance to cracking.
IEC 60811-3-2: Loss of mass test - Thermal stability test.
UIC 895 OR: Technical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Individual screen||Copper tapes helically applied|
|Armour type||Aluminium Wire|
|Rated Voltage Uo/U (Um)||3.6/6 kV|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.C|
|Slightly halogenous||CSA 22.2 AG14 HCl < 14 %|
|Oil resistance||UIC 895 OR|
|Maximum operating temperature||90°C|
|See all products|