TECK90(XHHW-2)(AL) 600 V Multi core with bare ground conductor without outer sheath
General application as power cable in low voltage.
StandardsInternational : IEC 60332-1-2
National : CSA C22.2 N° 03-01; CSA C22.2 N° 131; CSA C22.2 N° 2556; CSA C22.2 N° 38; UL 2556
General application in low voltage distribution networks in operating stations where high mechanical strength is required. The interlocked aluminum armour gives greater flexibility compared to the traditional steel armour and the type of conformation of the same make has a high resistance to loads that could be placed on it.
1. Conductor: Compact aluminum 8000 series, class B.
2. Insulation: Anti-flame cross linked polyethylene XLPE type XHHW-2.
3. Grounding Conductor: Aluminum 8000 series, class B.
4. Inner covering: Anti-flame compound polyvinyl chloride PVC.
5. Armour: Interlocked aluminum tape.
Resistance to abrasion and oils. Resistance to weather and sunlight. Its armour provides additional mechanical protection and provides greater flexibility compared with other types of armour. Does not propagate the FT-1 flame. Fire retardant according to C22.2 No 0.3-01/FT-4. Resistance to attack by rodents.
For gauges equal to or smaller than 8 AWG: INDECO S.A. TECK 90(XLPE)(AL) (Nb. cores x Gauge phase cond. + Gauge ground. cond.) 0,6 kV XLPE Aluminum -25C FT1 FT4 SR CSA 255079 - Year - Sequential length.
For gauges higher than 8 AWG: INDECO S.A. TECK 90(XLPE)(AL) (Nb. cores x Gauge phase cond. + Gauge ground. cond.) 0,6 kV XLPE Aluminum -40C FT1 FT4 SR CSA 255079 - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black; red; blue.
CSA C22.2 Nº 131: Type TECK 90 cable.
CSA C22.2 Nº 38-05: Thermoset-insulated wires and cables.
CSA C22.2 Nº 03-01: Test methods for electrical wires and cables.
CSA C22.2 Nº 2556-07: Wire and cable test methods.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
UL 2556: Wire and Cable Test Methods. Section 18.104.22.168: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Aluminum 8000 series|
|Insulating material||Flame retardant XLPE|
|Inner sheath||Flame retardant PVC|
|Armour type||Interlocked aluminum tape|
|Time of application Dielectric strength core to screen DC||1min.|
|Mechanical resistance to impacts||Excellent|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||FT4 (C22.2 No. 0.3-01/4.11.4)|
|Bending factor when installed||12(xD)|
|Rodent protection||Corrugated aluminium tape|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|