StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; UL 2556
In low voltage power distribution networks. Special application in places with poor ventilation, direct application in places with public attendance high. It can be installed in ducts or directly underground in dry and wet places. Not recommended for outdoor installations.
1. Conductor: Soft copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Outer sheath: HFFR halogen free thermoplastic compound.
* Stranded conductors
The cable has excellent electric properties. The cross-linked polyethylene insulation allows a higher power capacity current under any operation conditions, lower dielectric losses, high insulation resistance. The outer sheath have the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils.
6 mm2 and 16 mm2.
INDECO S.A. FREETOX N2XOH 0,6/1 kV - 2 x 1 x section - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black and white.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy. Section 6.4.2: Oil Immersion Test.
|Conductor material||Soft copper|
|Individual sheath||Halogen free thermoplastic compound|
|Sheath colour||Individual sheath White-Black|
|Halogen free||IEC 60754-1|
|Time of application Dielectric strength core to screen DC||5min.|
|Oil resistance||ICEA S-95-658|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|