StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ABNT NBR 6251 ; ABNT NBR 7286 ; ICEA S-93-639; NTP-IEC 60228; UL 2556
Power distribution in medium voltage, direct application in places with public attendance high. Not recommended for outdoor installations.
1. Conductor: Compact stranded copper, class 2 (with longitudinally watertight between and over the conductor).
2. Inner semi-conductor: Extruded.
3. Insulation: High density Ethylene-propylene rubber HEPR.
4. External semi-conductor: Extruded strippable.
5. Screen: Copper wires + copper tape in open spiral (with longitudinally watertight under and over the screen).
6. Outer sheath: HFFR halogen free thermoplastic compound.
Good resistance to electric shock. With longitudinally watertight between and over the conductor; and under and over the screen.Excellent properties against heat aging. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils.
INDECO S.A. FREETOX NGSOH(2OL) 15/25 kV Section - PH(Section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
ABNT NBR 6251: Insulated power cables for rated voltages 1 kV up to 35 kV - Constructive requirements.
ABNT NBR 7286: Power cables with extruded ethylene rubber insulation (EPR) for rated voltages from 1 kV up to 35 kV - Perfomance requirements.
ANDE N° 03.24.29: Low voltage single-pole copper cable for use in substations.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Determination of degree of acidity of gases evolved during the combustion of materials taken from electric cables by measuring pH and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
|Conductor material||Soft copper|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper wire + copper tape|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||61.0kV|
|Time of application Dielectric strength core to screen DC||15min.|
|Voltage for partial discharge test||31.0kV|
|Maximal partial discharge test||3pC|
|Oil resistance||ICEA S-93-639|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Maximum operating temperature||105°C|
|Overload maximum core temperature||140°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|