StandardsInternational : IEC 60228; IEC 60332-1; IEC 60332-3 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034
National : ICEA S-93-639; NTP-IEC 60228; UL 1581
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded aluminium 1350, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper tapes.
6. Outer sheath: HFFR thermoplastic compound.
Conductor temperature of 90ºC for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Excellent properties against heat aging. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. The outer sheath has the following characteristics: low emission dense smoke and halogen free. Flame retardant.
INDECO S.A. NA2XSOH 35 kV 133% - 3x1xGauge - Year - Sequential length.
Non returnable wooden reels.
Insulation: Natural (Core identification with binder tapes: yellow (R), blue (S), red (T)).
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Determination of degree of acidity of gases evolved during the combustion of materials taken from electric cables by measuring pH and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
ICEA S-93-639 Section 9.4.2 (Oil Immersion Test): 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy - Oil Immersion Test.
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper tape, helically|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.C|
|Oil resistance||ICEA S-93-639|
|Maximum operating temperature||90°C|
|See all products|