StandardsInternational : IEC 60228; IEC 60332-1; IEC 60502-2; IEC 60754-1; IEC 60754-2; IEC 60811-1-1; IEC 60811-1-2; IEC 60811-1-3; IEC 61034
National : ICEA S-93-639; NTP-IEC 60228; NTP-IEC 60502-2
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded soft copper, class 2.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper wires.
6. Tape: Polyester.
7. Outer sheath: Low Density Polyethylene .
Conductor temperature of 90ºC for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. The outer sheath has the following characteristics: low emission dense smoke and halogen free. Flame retardant.
From 50 mm2 up to 240 mm2.
INDECO S.A. N2XS2Y 6/10 kV - Section - PH(Screen section) - Year
Non returnable wooden reels.
Outer sheath: Red.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
ICEA S-93-639 Section 9.4.2 (Oil Immersion Test): 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy - Oil Immersion Test.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-1-2: Thermal ageing methods.
IEC 60811-1-3: Water absorption tests - Shrinkage test.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Halogen free||IEC 60754-1|
|Rated Voltage Uo/U (Um)||6/10 kV|
|Smoke density||IEC 61034-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Flame retardant||IEC 60332-1|
|Oil resistance||ICEA S-93-639|
|Maximum operating temperature||90°C|
|See all products|