StandardsInternational : IEC 60332-1; IEC 60332-3 Cat.C; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034
National : ASTM B 231; ICEA S-66-524; ICEA S-93-639; ICEA S-94-649
Power distribution in medium voltage, direct application in places with public attendance high. Not recommended for outdoor installations.
1. Conductor: Compact stranded 1350 aluminium, class B (longitudinally watertight between and over conductor).
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Concentric conductor: Copper wires helically applied. (1/3) Concentric neutral according to ICEA S-94-649 (longitudinally watertight under and over concentric conductor).
6. Outer sheath: HFFR-UV thermoplastic compound.
Conductor temperature of 90ºC for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Longitudinally watertight between and over phase conductor; and under and over concentric conductor. To 133% for insul level. Resistance to sunlight and oils. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free.
INDECO S.A. FREETOX NA2XCOH(2OL) 15 kV 133% I.L. - Gauge - NC33 - Year
Non returnable wooden reels.
Outer sheath: Red-UV.
ASTM B231: Standard specification for concentric-lay-stranded aluminum 1350 conductors.
ICEA S-66-524: Cross Linked Thermosetting Polyethylene Insulated Wire and Cable for the Transmission and Distribution of Electrical Energy.
ICEA S-93-639 Section 9.4.2 (Oil Immersion Test): 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy - Oil Immersion Test.
ICEA S-94-649: Concentric neutral Cables rated 5 through 46 kV.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
FENOSA standard ES.03427.CO: Insulated conductors for underground medium voltage lines.
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Concentric conductor||Copper wires helically applied|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.C|
|Longitudinal water tightness||Yes|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Oil resistance||ICEA S-93-639|
|Maximum operating temperature||90°C|
|See all products|
Products and services
Docs and info
Concentric Neutral Nb of wires