NAYY(80º) 0,6/1 kV Multicore with isolated ground. cond.; UIC 895OR; Anixter
General use as power cable, for fixed installations.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-1; SAE J-1127; UL 2556; UL 44
General use as power cable. In low voltage distribution networks, industrial installations, buildings and operating centers. For fixed installations, in indoor areas (trays, gutters, staples), outdoors, in underground ducts or buried direct in ground. It can also be installed in dry or wet locations.
1. Conductor: Compact stranded 1350 aluminium, class 2.
2. Insulation: Compound polyvinyl chloride PVC.
3. Insulated grounding conductor: Compact round aluminium 1350, class 2 - PVC.
4. Filler: Anti-flame compound polyvinyl chloride PVC.
5. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Good electrical and mechanical properties. The PVC outer sheath allows an adequate resistance to abrasion, moisture and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Resistant to gasoline GR I according to UL 44. Flame retardant.
150 mm2 and 240 mm2.
INDECO S.A. NAYY(80°) 0.6/1 kV - 3 x (fase cond. section) + 1 x (grounding cond. section) - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3 kV.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556: Wire and Cable Test Methods. Section 126.96.36.199: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Time of application Dielectric strength core to screen DC||5min.|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Oil resistance||UIC 895 OR|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|
Products and services
Docs and info
Core Identification L.V with ground conductor
Number of cores
White + black + (green)
White + black + red + (green)
White + black + red + blue + (green)