FREETOX N2XRAOH 0.6/1 kV Single core; Anti-Rodent
General application as power cable of low voltage. Special application in installations with poor ventilation, direct application in places with high public attendance.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60332-3 Cat.C; IEC 60502-1; IEC 60684-2; IEC 60754-1; IEC 60754-2; IEC 61034
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operating stations, indoor and outdoor areas. Special application in installations with poor ventilation, direct application in places with high public attendance. It can be installed in ducts, in dry or wet locations where mechanical strength is required. Not recommended for outdoor installations.
1. Conductor: Soft copper, class 2.
2. Insulation: Anti-flame cross linked polyethylene XLPE.
3. Inner covering: Thermoplastic compound HFFR.
4. Armour: 1350 aluminium wires.
5. Tape: Polyester tape.
6. Outer sheath: HFFR thermoplastic anti-rodent compound.
Good electrical and mechanical properties. Its armour provides additional mechanical protection. Resistance to abrasion and sunlight. The outer sheath has the following characteristics: Fire retardant, low emission dense smoke and halogen free. Adequate resistance to oils. Resistance to attack by rodents.
From 10 mm2 up to 25 mm2.
INDECO S.A. N2XRAOH 0.6/1 kV - Cross Section - Year - Sequential Length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables
NPT-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3 kV.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658 Section 6.4.2 (Oil Immersion Test): Power cables rated 2000 volts or less for the distribution of electrical energy - Oil Immersion Test.
|Armour type||Aluminium Wire|
|Outer sheath||Halogen free thermoplastic compound|
|Halogen free||IEC 60754-1|
|Mechanical resistance to impacts||Good|
|Rodent protection||ARS (Anti rodent sheath)|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.C|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|