N2XRY 0,6/1 kV Multicore; IEC 60332-3-22 Cat. A; ANti-termite; PMRT
General application as low voltage power cable.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60332-3 Cat.A; IEC 60502-1; IEC 60754-1; IEC 60811-1-1; IEC 60811-1-2; IEC 60811-1-3; IEC 60811-1-4; IEC 60811-2-1; IEC 60811-3-1; IEC 60811-3-2; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 1581; UL 44
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operating stations, indoor and outdoor areas. It can be installed in ducts, in dry or wet locations where mechanical strength is requiered.
1. Conductor: Soft copper, class 2.
2. Insulation: Cross linked polyethylene XLPE.
3. Insulated grounding conductor - Cross linked polyethylene XLPE.
4. Cabling: Insulated phases + Polypropylene thread + Fiberglass tape.
5. Inner covering: Anti-flame compound polyvinyl chloride PVC.
6. Armour: Galvanized steel wires + Polyester tape.
7. Outer sheath: Anti-flame and anti-termite PVC.
Good electrical and mechanical properties. Its armour provides additional mechanical protection. Resistance to abrasion and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR and Gasoline Resistant GR I according to UL 44. Fire retardant according to IEC 60332-3 CAT A. Low halogen content according to IEC 60754-1. Resistance to attack by termites.
INDECO S.A. N2XRY 0.6/1 kV - Nb. cores x section - Year - Sequential length.
Non returnable wooden reels.
Insulation: Blue, black and yellow/green.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables
NPT-IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages from 1 kV and 3kV.
IEC 60228: Conductors of insulated cables.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-22: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category A.
IEC 60502-1: Power cables with extruded insulation and their accesories for rated voltages of 1 kV and 3 kV.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-1-2: Thermal ageing methods.
IEC 60811-1-3: Water absorption tests - Shrinkage test.
IEC 60811-1-4: Tests at low temperature.
IEC 60811-2-1: Ozone resistance, hot set and mineral oil inmersion tests.
IEC 60811-3-1: Pressure test at high temperature - Tests for resistance to cracking.
IEC 60811-3-2: Loss of mass test - Thermal stability test.
UIC 895 OR: Techical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Inner sheath||Flame retardant PVC|
|Armour type||Galvanized steel wires|
|Outer sheath||Flame retardant Antitermite PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Mechanical resistance to impacts||Good|
|Fire retardant||IEC 60332-3 Cat.A|
|Flame retardant||IEC 60332-1|
|Slightly halogenous||IEC 60754-1|
|Oil resistance||UIC 895 OR|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|Resistant to termites||Yes|
|See all products|