StandardsInternational : IEC 60228; IEC 60332-1; IEC 60502-1; IEC 60754-1; IEC 60811-1-1; IEC 60811-1-2; IEC 60811-1-3; IEC 60811-1-4; IEC 60811-2-1; IEC 60811-3-1; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-1; UL 1581
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations, where mechanical strength is required.
1. Conductor: Soft copper, class 5.
2. Insulation: Cross linked polyethylene XLPE.
3. Inner covering: Anti-flame compound polyvinyl chloride PVC.
4. Armour: Aluminium tapes.
5. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Conductor temperature of 90°C for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Excellent properties against heat aging. Its armor provides additional mechanical protection. Resistance to abrasion, moisture and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR. Flame retardant.
INDECO S.A. N2XBAY 0.6/1 kV - Section - FB - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-1-2: Thermal ageing methods.
IEC 60811-1-3: Water absorption tests - Shrinkage test.
IEC 60811-1-4: Tests at low temperature.
IEC 60811-2-1: Ozone resistance, hot set and mineral oil immersion tests.
IEC 60811-3-1: Pressure test at high temperature - Tests for resistance to cracking.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
UIC 895 OR: Technical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Copper class 5|
|Inner sheath||Flame retardant PVC|
|Armour type||Double aluminium tape|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Flame retardant||IEC 60332-1|
|Oil resistance||UIC 895 OR|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|