CAPI-MT(OL) 35 kV; WITH SEMI-CONDUCTOR; ABNT NBR 11873
For overhead primary distribution networks.
StandardsInternational : IEC 60228
National : ABNT NBR 11873; ICEA T-31-610; NTP-IEC 60228
For overhead primary distribution networks in horizontal arrangements. The installation will be performed in wooded areas in order to reduce the contact of environmental impact. This is not an insulated cable, it is a protected cable.
1. Conductor: Compact stranded aluminium 1350, class 2 (with longitudinally watertight between the conductor).
2. Semi-conductor: Extruded.
3. Sheath: Antitracking cross linked polyethylene XLPE compound.
With longitudinally watertight between the conductor. Good properties against heat aging. Resistance to abrasion, moisture, sunlight and to surface discharges (tracking and carbonization). Protection should not be considered as insulation.
70 mm2,150 mm2 y 185 mm2.
INDECO S.A. CAPI-MT(OL) - Protected Cable 35 kV, Do not Touch - Section - Year - Sequential length.
Non returnable wooden reels.
NTP-IEC 60228: Conductors of insulated cables.
IEC 60228: Conductors of insulated cables.
ABNT-NBR 11873: Covered cables with polymeric material for overhead distribution lines in spacers for voltages 13,8 kV up to 34,5 kV.
ICEA T-31-610: Test method for conducting longitudinal water penetration resistance tests on blocked conductors.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Time of application Dielectric strength core to screen DC||5min.|
|Longitudinal water tightness||Conductor ICEA T-31-610|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|