NA2XR2Y 600 V Multicore; 8000 series Alum.; Outer sheath: LLDPE; UV Resist.
General application as power cable in low voltage.
StandardsInternational : IEC 60332-1; IEC 60754-1; IEC 60754-2; IEC 61034
National : ASTM B 800; ASTM B 801; ICEA S-95-658; UL 1581
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operating stations, indoor and outdoor areas. It can be installed in ducts, in dry or wet locations where mechanical strength is required.
1. Conductor: Aluminium 8000 series, class B.
2. Insulation: Cross linked polyethylene XLPE.
3. Inner covering: High density polyethylene HDPE-UV.
4. Armour: Galvanized steel wires.
5. Tape: Polyester tape.
6. Outer sheath: High density polyethylene HDPE-UV.
Good electrical and mechanical properties. Cross-linked polyethylene insulation allows greater power capacity under any operating condition, minimum dilelectric losses, high insulation resistance. Its armour provides additional mechanical protection. The HDPE outer sheath has the following characteristics: good thermal and chemical resistance. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. Flame retardant.
INDECO S.A. NA2XR2Y 600 V - Nb conductors x Gauge - Year.
Non returnable wooden reels.
Insulation: Black, Blue and Red.
Outer sheath: Black.
ASTM B 800: Standard Specification for 8000 Series Aluminum Alloy wire for Electrical Purposes.
ASTM B 801: Standard Specification for Concentric-Lay-Stranded Conductors of 8000 series Aluminum Alloy for subsequent covering or Insulation.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables - Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-95-658 Section 6.4.2 (Oil Immersion Test): Power cables rated 2000 volts or less for the distribution of electrical energy - Oil Immersion Test.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Aluminum 8000 series|
|Armour type||Galvanized steel wires|
|Halogen free||IEC 60754-1|
|Rated Voltage Uo/U (Um)||600 V|
|Mechanical resistance to impacts||Good|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1|
|Oil resistance||ICEA S-95-658|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|