NGY 0,6/1 kV Single-core FB; ABNT NBR 6251; ABNT NBR 7286 Outher sheath antiflame
General use as power cable, for fixed installations.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60811-1-1; IEC 60811-1-2; IEC 60811-1-4; IEC 60811-2-1; IEC 60811-3-2; UIC 895
National : ABNT NBR 6251 ; ABNT NBR 7286 ; NTP-IEC 60228; UL 1581
General application as power cable. In low voltage distribution power networks, industrial installations, in buildings and operation stations. In fixed installations, indoor and outdoor areas (trays, gutters, staples). It can be installed in ducts, in dry or wet locations.
1. Conductor: Soft copper, class 5.
2. Insulation: HEPR.
3. Outer sheath: Flame retardant PVC compound.
HEPR increased safety due to its mechanical strength and toughness of the insulation. Excellent properties against heat aging. Adequate resistance to abrasion, moisture and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR. Flame retardant.
INDECO S.A. NGY 0.6/1 kV - Section - FB - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
ABNT NBR 6251: Insulated power cables, for rated voltages 1 kV up to 35 kV - Constructive requirements.
ABNT NBR 7286: Power cables with extruded ethylene rubber insulation (EPR) for rated voltages from 1 kV up to 35 kV - Performance requirements.
IEC 60228: Conductors of insulated cables.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-1-2: Thermal ageing methods.
IEC 60811-1-4: Tests at low temperature.
IEC 60811-2-1: Ozone resistance, hot set and mineral oil immersion tests.
IEC 60811-3-2: Loss of mass test - Thermal stability test.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
UIC 895 OR: Technical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor flexibility||Flexible class 5|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Flame retardant||IEC 60332-1|
|Oil resistance||UIC 895 OR|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|