NAGS2Y 18/30 kV PH+PC; LLDPE Outer Sheath; UV Resist.; UNE-HD 620-9E
Power distribution in medium voltage.
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-2; IEC 60754-1; IEC 60754-2; IEC 61034-2
National : ICEA S-93-639; NTP-IEC 60228; NTP-IEC 60502-2; UL 2556; UNE-HD 620
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded aluminium 1350, class 2.
2. Inner semi-conductor: Extruded.
3. Insulation: High Density Ethylene-Propylene Rubber HEPR.
4. External semi-conductor: Extruded strippable.
5. Screen: Copper wires + Copper tape.
6. Tape: Polyester tape.
7. Outer sheath: LLDPE-UV linear low density polyethylene.
Excellent properties against heat aging. Good resistance to electric shock. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. The outer sheath has the following characteristics: low emission dense smoke and halogen free. Flame retardant.
From 95 mm2 up to 500 mm2.
INDECO S.A. NAGS2Y 18/30 kV - Section - PH(Section) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Red-UV.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
UNE-HD 620-9E: Distribution cables with extruded insulation for rated voltages from 3,6/6 (7,2) kV up to and including 20,8/36 (42) kV. Part 9: HEPR insulated single core cables, and single core pre-assembled cables. Section E: Cables with polyolefine compound sheath (types 9E-1, 9E-3,9E-4 and 9E-5).
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60684-2: Flexible insulating sleeving - Part 2: Methods of test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables. Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Test on gases evolved during combustion of materials from cables. Part 2: Determination of acidity (by pH measurement) and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639: 5-46 kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy. Section 9.4.2: Oil Immersion Test.
UL 2556: Wire and Cable Test Methods. Section 22.214.171.124: Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||aluminum Alloy 1350|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper wire + copper tape|
|Sheath colour||Red - UV|
|Halogen free||IEC 60754-1|
|Dielectric strength core to screen DC, min.||63.0kV|
|Time of application Dielectric strength core to screen DC||5min.|
|Voltage for partial discharge test||31.1kV|
|Maximal partial discharge test||10pC|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Oil resistance||ICEA S-93-639|
|Gases toxicity||Low toxicity to IEC 60684-2|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1-2; FT1|
|Maximum operating temperature||105°C|
|Overload maximum core temperature||140°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|