StandardsInternational : IEC 60332-1; IEC 60754-1; IEC 60754-2; IEC 61034
National : ASTM B 3; ASTM B 8; ICEA S-93-639; ICEA S-94-649; UL 1581
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded soft copper, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Concentric conductor: Copper wires helically applied. (1/3) Concentric neutral according to ICEA S-94-649.
6. Tape: Polyester.
7. Outer sheath: High density polyethylene HDPE-UV.
Conductor temperature of 90ºC for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. 100% for insulation level. Excellent properties against heat aging. Resistance to abrasion, moisture and sunlight. Adequate resistance to greases and oils. The outer sheath has the following characteristics: low emission dense smoke and halogen free. Flame restardant.
250 kcmil and 1000 kcmil.
INDECO S.A. N2XC2Y 15 kV - Gauge - NC33 - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
ASTM B3: Soft Annealed Copper Wire.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
NO.MA.08.09: Cable for medium voltage copper with concentric neutral.
ICEA S-94-649: Concentric Neutral Cables Rated 5 Through 46 kV.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
IEC 60754-2: Determination of degree of acidity of gases evolved during the combustion of materials taken from electric cables by measuring pH and conductivity.
IEC 61034-2: Measurement of smoke density of cables burning under defined conditions.
ICEA S-93-639 Section 9.4.2 (Oil Immersion Test): 5-46kV Shielded Power Cable for Use in the Transmission and Distribution of Electric Energy - Oil Immersion Test.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Concentric conductor||Copper wires helically applied|
|Halogen free||IEC 60754-1|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Oil resistance||ICEA S-93-639|
|Gases corrosivity||Low pH Corrosivity IEC 60754-2|
|Smoke density||IEC 61034-2|
|Flame retardant||IEC 60332-1|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|
Products and services
Docs and info
Concentric Neutral Nb of wires