StandardsInternational : FT4 IEEE1202 ; IEC 60228; IEC 60332-1; IEC 60502-2; IEC 60811-1-1; IEC 60811-1-2; IEC 60840; UIC 895
National : NTP-IEC 60228; NTP-IEC 60502-2; SAE J-1127; UL 1581
Power distribution in medium voltage. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas and mining installations, in dry or wet locations.
1. Conductor: Compact stranded soft copper, class 2.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion in dry cure process.
5. Screen: Copper tapes (with longitudinally watertight under and over the screen).
6. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Conductor temperature of 90ºC for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Longitudinally watertight between and over screen. Resistance to abrasion, moisture and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127 standard. Fire retardant.
70 mm2 and 150 mm2.
INDECO S.A. N2XSY(F) 26/45 kV - Section - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-2: Power cables with extruded insulation and their accessories for rated voltages from 6 kV up to 30 kV.
IEC 60840: Power cables with extruded insulation and their accessories for rated voltages above 30 kV (Um = 36 kV) up to 150 kV (Um = 170 kV) - Test methods and requirements.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
FT4/IEEE 1202: Vertical tray flame test.
IEC 60811-1-1: Measurement of thickness and overall dimensions - Test for determining the mechanical properties.
IEC 60811-1-2: Thermal ageing methods.
SAE J1127: Surface vehicle standard. Battery cable. Clause 6.7 (Fluid Compatibility) - Resistance to Sulfuric Acid.
UIC 895 OR: Technical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Screen||Copper tape, helically|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||26/45 kV|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Longitudinal water tightness||Yes|
|Flame retardant||IEC 60332-1|
|Fire retardant||FT4 (C22.2 No. 0.3-01/4.11.4)|
|Oil resistance||UIC 895 OR|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|