NYY(80º) 600 V Multicore; IEC 60332-3-24 Cat C.
General use as power cable, for fixed installations.
StandardsInternational : IEC 60332-1-2; IEC 60332-3-24 Cat.C; IEC 60754-1; UIC 895
National : ASTM B 8; ICEA S-95-658; SAE J-1127; UL 2556; UL 44
General use as power cable. In low voltage distribution networks, industrial installations, buildings and operating centers. For fixed installations, in indoor areas (trays, gutters, staples), outdoors, in underground ducts or buried direct in ground. It can also be installed in dry or wet locations.
1. Conductor: Compressed soft copper, class B.
2. Insulation: Compound polyvinyl chloride PVC.
3. Inner sheath: Anti-flame compound polyvinyl chloride PVC..
4. Outer sheath: Anti-flame compound polyvinyl chloride PVC..
Good electrical and mechanical properties. The PVC outer sheath provides an adequate resistance to grease, oils, abrasion and sunlight. RResistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Fire retardant according to IEEE 1202/FT-4.
16 AWG and 12 AWG.
INDECO S.A. NYY(80º) 600 V - Nb. Cores x gauge - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
FT4/IEEE 1202: Vertical Tray Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 22.214.171.124:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Inner sheath||Flame retardant PVC|
|Outer sheath||Flame retardant PVC|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||IEC 60332-3-24 Cat.C|
|Oil resistance||UIC 895 OR|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|
Products and services
Docs and info
Core Identification L.V
Number of cores
White + black
White + black + red
White + black + red + blue