TCS(RHW-2) 2 kV VFD; FT4/IEEE 1202
Power or control cable, for use with variable frequency drives (VFD).
StandardsInternational : FT4 IEEE1202 ; IEC 60332-1-2; IEC 60754-1; UIC 895
National : ASTM B 8; SAE J-1127; UL 1277; UL 2556; UL 44
In factories, substations or power plants where there is a lot of electrical noise or transiet, for control, measuring or signaling systems, for connection between the variable frequency drive (VFD) and the motor; reduce electromagnetic interferences. Maximum operating temperature 90°C, in dry or wet locations.
1. Conductor: Soft copper, class B.
2. Insulation: Anti-flame Cross linked polyethylene XLPE.
3. 03 Bare grounding conductors: Soft Copper, class B.
4. Inner sheath: Anti-flame Compound polyvinyl chloride PVC.
5. Screen: Copper tapes (30mm x 0.127mm) 50% overlapped.
6. Outer sheath: Anti-flame Compound polyvinyl chloride PVC.
Excellent properties against heat aging. Adequate to transient shield. Resistance to moisture, abrasion and sunlight. Resistance to liquid fuels and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Low halogen content according to IEC 60754-1. Resistant to gasoline GR I according to UL 44. Fire retardant according to IEEE 1202/FT-4.
From 14 AWG up to 750 kcmil.
INDECO S.A. TCS(RHW-2) 2kV - (Nb. Cores x gauge) + (3x ground. cond. gauge) - Year - Sequential length.
Non returnable wooden reels.
Insulation: Black, red, blue.
Outer sheath: Black.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard, medium-hard, or soft.
UL 1277: Electrical Power and Control Tray Cables with Optional Optical-Fiber Members.
UL 44: Thermoset-Insulated Wires and Cables.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
UL 2556: Wire and Cable Test Methods. Section 9.3: FT1 (Vertical-Specimen) Flame Test.
IEC 60754-1: Test on gases evolved during combustion of materials from cables - Part 1: Determination of the halogen acid gas content.
FT4/IEEE 1202: Vertical Tray Flame Test.
SAE J1127: Standard for Vehicle Cables. Battery cable Clause 6.7 (Compatibility of fluids) - Resistance to Sulfuric Acid.
UL 44: Thermoset-Insulated Wires and Cables. Section 5.17: Gasoline and oil resistance.
UIC 895 OR: Technical specifications for the supply of insulated electric cables for railway vehicles - Oil resistance.
UL 2556:Wire and Cable Test Methods. Section 188.8.131.52:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Insulating material||Flame retardant XLPE|
|Inner sheath||Flame retardant PVC|
|Electrostatic shielding||Copper tapes helically applied|
|Outer sheath||Flame retardant PVC|
|Slightly halogenous||IEC 60754-1|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Electro magnetic interference resistance||Yes|
|Flame retardant||IEC 60332-1-2; FT1|
|Fire retardant||FT4 (C22.2 No. 0.3-01/4.11.4)|
|Oil resistance||UIC 895 OR|
|Fuel resistance||GR I - UL44|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|