NYY(80º) 0,6/1 kV Multicore with grounding conductor; IEC 60332-3-24
General use as power cable, for fixed installations.
StandardsInternational : IEC 60228; IEC 60332-1; IEC 60332-3-24 Cat.C; IEC 60502-1; UIC 895
National : ICEA S-95-658; NTP-IEC 60228; NTP-IEC 60502-1; SAE J-1127; UL 1581
General use as power cable. In low voltage distribution networks, industrial installations, buildings and operating centers. For fixed installations, in indoor areas (trays, gutters, staples), outdoors, in underground ducts or buried direct in ground. It can also be installed in dry or wet locations.
1. Conductor: Soft copper, class 2.
2. Insulation: Compound polyvinyl chloride PVC.
3. Insulated grounding conductor: Copper - PVC.
4. Inner sheath: Anti-flame compound polyvinyl chloride PVC..
5. Outer sheath: Anti-flame compound polyvinyl chloride PVC..
Good electrical and mechanical properties. The PVC outer sheath provides an adequate resistance to grease, oils, abrasion and sunlight. Resistance to oil according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Fire retardant.
From 1.5 mm2 up to 16 mm2.
INDECO S.A. NYY(80º) 0.6/1 kV - Nb. Cores x gauge + ground section - Year - Sequential length.
Non returnable wooden reels.
Insulation: See core identification.
Outer sheath: Black.
NTP-IEC 60228: Conductors of insulated cables.
NTP-IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
IEC 60228: Conductors of insulated cables.
IEC 60502-1: Power cables with extruded insulation and their accessories for rated voltages from 1 kV and 3 kV.
ICEA S-95-658: Power cables rated 2000 volts or less for the distribution of electrical energy.
IEC 60332-1: Test for vertical flame propagation for a single insulated wire or cable.
IEC 60332-3-24: Test for vertical flame spread of vertically-mounted bunched wires or cables - Category C.
SAE J1127: Surface vehicle standard. Battery cable. Clause 6.7 (Fluid Compatibility): Resistance to Sulfuric Acid.
UIC 895 OR: Techical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
UL 1581 Section 1200 (Sunlight resistance): Reference standard for electrical wires, cables, and flexible cords - Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Inner sheath||Flame retardant PVC|
|Outer sheath||Flame retardant PVC|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|U.V resistance||UL 1581 - Sunlight Resistance|
|Oil resistance||UIC 895 OR|
|Flame retardant||IEC 60332-1|
|Fire retardant||IEC 60332-3 Cat.C|
|Maximum operating temperature||80°C|
|Overload maximum core temperature||100°C|
|Short-circuit max. conductor temperature||160°C|
|See all products|
Products and services
Docs and info
Core Identification L.V with ground cond.
Number of cores
White + black + (yellow or green or yellow/green or green/yellow)
White + black + red + (yellow or green or yellow/green or green/yellow)
White + black + red + blue + (yellow or green or yellow/green or green/yellow)