N2XSEYBAIY(INTERLOCK) 5 kV 133% I.L.; 3F +3G; FT4/ IEEE 1202
Power distribution in medium voltage.
StandardsInternational : FT4 IEEE1202 ; IEC 60332-1-2; UIC 895
National : ASTM B 8; ICEA S-93-639; SAE J-1127; UL 1072; UL 2556
Power distribution in medium voltage. To 133% for insulation level. As transformer feeders in substations. In power plants, industrial and operation installations, in residential areas mining installations where high mechanical strength is required. The interlocked aluminum armour gives greater flexibility compared to the traditional steel armour and the type of conformation of the same make has a high resistance to loads that could be placed on it.
1. Conductor: Round compact soft copper, class B.
2. Inner semi-conductor: Extruded.
3. Insulation: Cross linked polyethylene XLPE-TR (Tree retardant).
4. External semi-conductor: Extruded strippable.
These last three components extruded CV (continuous vulcanization) triple extrusion.
5. Screen: Copper tapes.
6. 03 Bare grounding conductor: Soft copper, class B.
7. Separation sheath: Anti-flame compound polyvinyl chloride PVC.
8. Armour: Interlocked aluminum tape.
9. Outer sheath: Anti-flame compound polyvinyl chloride PVC.
Conductor temperature of 90°C for normal operation, 130°C for emergency overload and 250°C for short circuit conditions. Its armour provides additional mechanical protection and provides flexibility compared with other types of armour. Excellent properties against heat aging. Resistance to abrasion; moisture and sunlight. Resistance to combustible liquids and oils according to UIC 895 OR. Resistance to sulfuric acid according to SAE J1127. Adequate resistance to greases and oils. Fire retardant - type FT4. Resistance to attack by rodents.
INDECO S.A. N2XSEYBAIY(INTERLOCK) 5 kV 133% – (Nb. Cores x gauge) + (3x ground. cond. gauge) - Year - Sequential length.
Non returnable wooden reels.
Outer sheath: To customer request.
ASTM B8: Concentric-Lay-Stranded copper conductors, hard; medium-hard; or soft.
UL 1072: Standard for Medium-Voltage Power Cables.
ICEA S-93-639: 5 - 46 kV Shielded Power Cable for use in the transmission and distribution of electric energy.
IEC 60332-1-2: Test for vertical flame propagation for a single insulated wire or cable - Procedure for 1 kW pre-mixed flame.
FT4/IEEE 1202: Vertical Tray Flame Test.
SAE J1127: Surface vehicle standard. Battery cable. Clause 6.7 (Fluid Compatibility) : Resistance to Sulfuric Acid.
UIC 895 OR: Techical specification for the supply of insulated electric cables for railway vehicles - Oil Resistant.
UL 2556:Wire and Cable Test Methods. Section 22.214.171.124:Carbon-Arc and Xenon-Arc Tests- Sunlight resistance.
|Conductor material||Soft copper|
|Material of the inner semi-conductor||Extruded|
|Material of the external semi-conductor||Extruded strippable|
|Individual screen||Copper tapes helically applied|
|Inner sheath||Flame retardant PVC|
|Armour type||Interlocked aluminum tape|
|Outer sheath||Flame retardant PVC|
|Mechanical resistance to impacts||Excellent|
|U.V resistance||UL 2556 - Sunlight Resistance|
|Flame retardant||IEC 60332-1-2|
|Fire retardant||FT4 (C22.2 No. 0.3-01/4.11.4)|
|Oil resistance||UIC 895 OR|
|Rodent protection||Corrugated aluminium tape|
|Maximum operating temperature||90°C|
|Overload maximum core temperature||130°C|
|Short-circuit max. conductor temperature||250°C|
|See all products|